They use Thermaco
"Superceptor®" grease/oil separators with Edson International
diaphragm pumps to extract the solids and grease in their waste water.
Using the Thermaco system maintains a clean waste stream and keeps restaurants,
like theirs, in compliance with local discharge limitations of oil, grease
and like products.
The unit pictured below is one of several installed by Diversified
Sales, Woodbridge, CT at Mohegan Sun.
pumps were selected for their superior ability to handle solids(food particles),
and viscous liquids (grease and oils).
The solids handling capabilities, non-emulsifying action and proven reliability
make it a perfect fit for separator units like these.
Pump Used: 120ELA-40-200
Pump Setup: Pump
Data Sheets Wetted Surface - Anodized Aluminum (w/white
Inlet - 2" MNPT Discharge - 2" FNPT
Motor - 1/2HP/1ph/120-240V/TEFC
Head - 15ft Suction / 15ft Discharge / 12ft Dry
Cycle Speed - 30 cycles per min. with a 57 to 1 reducer
Performance - 20 gpm at 30 Cycles per min